Addressable Manual I-9201 Call Point Technical Specifications
• • • • •
B-9201 Features and Benefits 1. 2. 3. 4. 5. 6.
Re-settable (non-breaking glass) Additional volt free contact Electronically addressed Friendly installation and test Suitable for semi-flush and surface mount installation Stylish pleasing design
Description: Designed for the purpose of raising an alarm manually once verification of a fire or emergency condition has occurred. By pressing the non breakable glass. The I-9201 constructed of high impact red ABS and smooth shiny appearance on the surface. Stylish pleasing design and easy to install for modern building interior. Complete with terminating back box enables first fix installation and termination leaving the fascia with integral electronics to be simply plugged into pace at the time of commissioning. Non breakable glass that can be reset with the GST standard reset tool. The I-9201 operated via a micro-switch that when pressed a signal will be transmitted and the volt free contact will be latched. Contain integral LED indicator to denote operational mode. Electronic addressing can be done through Handheld Programming device (P-9910), purchased separately.
• • • • • • • •
Protection rating: IP 30 Operating voltage: 24Vdc Loop voltage Operating current: Standby current 0.8mA Alarm Current 2mA Operating temperature: -10°C to +50°C N/O Output contact: 60Vdc, 0.1A Contact resistance: 100mΩ Relative humidity: 95% Application: Indoor use Visual Indicator: LED, Red ( lit steady when alarm, 3 sec interval blinking at normal state) Material and colour: ABS, red Wiring: 1 pair non polarized Dimensions: 90x122x48.5mm
Mounting Base The manual call point should be installed in compliance with all local codes having a jurisdiction in your area or NFPA 72 National Fire Alarm Code, NFPA 70 National Electrical Code, BS 5389 and EN54. Surface mount and it is installed onto a standard one gang electrical box with a mounting hole that has 52mm~68mm spacing.
ELECTRICAL BACK BOX
I−9201 WALL FIRE
B−9201 BACK BOX
SEMI FLUSH MOUNT
Addressable Manual I-9201 Call Point Selection of compatible Control Panels
Wiring and Connection Connect the wires to the required terminal according to the wiring diagram. The Z1, Z2 is for addressable Loop, non-polarized while the K1, K2 is intended to normally open passive contacts, can provide DC 500mA control signal when the 24VDC power bus is connected. The cable must be fire rated type and the size depends on the distance and application. Minimum size gauge 1.0mmÂ˛
10 11 12
Compatible with all GST Fire Alarms Panels GST 100, GST 200, GST 5000, GST 9000. Ordering Information: Part No
Addressable Manual Call Point Semi-flush Mount Box
Pack Qty per Box 120 120
K1 K2 Z1 Z2
Programming The address of the manual call point can be programmed using GST handheld programmer (P-9910), purchased separately. Connect the two wires of the handheld programmer to Z1 and Z2 terminals of the manual call point (I-9102).
12 11 10
Z1 AND Z2 TERMINAL MANUFACTURED IN ACCORDANCE WITH
FIELD DEVICE PROGRAMMER
Note: Specifications are subject to change without notice.