DIGITAL ENERGY Power Quality FLASH SERVICE NEWS Nr. 10 2009 From: GE Digital Energy Power Quality CONCERNS: UPS Type and Series: Produced during periode: Reference Documentation:
Date: 30.07. 2009 To: GE Digital Energy Service Managers & Business Partners Inverter reliability. (routing of driver cables) Lanpro 33, 100 and 120kVA CE All UPSs produced before week 31/ 2009 See pictures on the next page
SHORT PROBLEM DESCRIPTION: Cables from the driver boards IM0107 or IM0110 connecting to the IGBTs shall not be tied together, but must run seperated from each other. See pictures on the next page for reference.
INTERVENTION LEVEL: ACTION ALERT
Failure to comply with this FSN could result in equipment damage and loss of Load. Immediate action has to be taken, including units in stock.
Action required , that if left uncorrected may reduce equipment reliability, efficiency, premature failure or even damage. Must be performed before startup and commissioning, and as soon as possible on running units.
Identifies maintenance interventions or best practice for reliable functionality of the equipment within a defined periode. Must be performed before startup and commissioning, and at next maintenance on running units.
Identifies changes or updates, which might be beneficial to some, but not necessarily to all equipment. Done at customers discretion.
Contact â€žSupport Centralâ€œ, if assistance is required, at the link: http://supportcentral.ge.com/products/sup_products.asp?prod_id=48055 This document is for the use of GE personnel and their Business Partners only, and shall neither be reproduced nor shown in whole or part for use without written permission of GE Digital Energy Services.
After the failure of some Inverter bridges, it was found that some UPSs Lanpro 33 CE, 100 and 120kVA, produced prior to week 31, year 2009, had the connection cables for the Inverter drive pulses tied together, although production directives did not specify this, neither was this the case in the homologated units. Extensive testing proved that the reliability and secure functionality of the Inverter could be reduced if the drive connection cables are not routed separately. We therefore highly recommand to verify at the earliest, on units produced previously of week 31, year 2009 the wiring connections of these drive pulse cables, and where necessary, to separate them. This can simply be done by cutting the straps used to tie them together. Attention: UPS must be shutdown, load can be supplied through Q2. The pictures below shall illustrate the above description.
Published on Dec 15, 2012