Figure 2: Flameless explosion suppression by the Q-Rohr
that the pressure and the flames cannot propagate and so that any adjoining parts of the plant are protected. A distinction is made between active and passive isolation systems. An active system is alerted to an explosion at an early stage, when an explosion begins to develop. This is done through sensors or detectors that register the rise in pressure or the formation of flames and respond by activating the relevant isolator, e.g. a quench valve. Passive isolation, on the other hand, responds purely mechanically to the spreading or loss of pressure, on account of its structural characteristics. This also applies to explosion valves. Under normal operation, an explosion valve in a pipeline is kept open by the available flow. When an explosion occurs, the valve is closed by the spreading of the pressure front, thus effectively prevents the pressure and the flames from propagating any further.
â€œIt is in the nature of a mill to have metallic parts that collide with one another at high speed, so that ignition sources are highly probable. Again, this is a closed container with a high concentration of dust, which may include oxygen, making an explosion extremely likely" Flameless venting
If a plant is situated within a building, however, explosion vents are not suitable for pressure relief purposes, as the safety area around them is inadequate to relieve the emerging dust and flames. Such an arrangement would pose an enormous safety risk to humans and machinery. This problem is often solved through the use of vent ducts, which channel the spread of an explosion to the outside. The disadvantage, however, is that it prevents any processoptimised plant design and is usually very expensive: the longer the distance between an explosion and its source, the higher the pressure which the vent duct and the plant need to withstand. This results in higher (production) costs for the vent duct. Flameless venting, on the other hand, is an option that is economical and effective. Different manufacturers use different technologies in flameless venting. Let us have a look at one particular technology at this point. The special mesh filter that is used in a Q-Box or Q-Rohr efficiently cools down any flames, preventing both flames and pressure from emerging and ensures particulate retention. The typical increase in pressure and noise that accompanies an explosion within a building is reduced to an almost imperceptible minimum, thus protecting both humans and machinery. In addition to the special stainless steel mesh filter, the Q-Rohr and Q-Box each have an explosion vent with an integrated signaling system that alerts the process control system when the explosion vent has opened. 78 | August 2017 - Milling and Grain