MR. MEGAWATT pressure. This points to some problem with condenser efficiency. her face and water all around her feet. I realized I might end up Based on this graph we thought we were on the right path. But sleeping with the fishes after all. ~ before we did our victory dance, we wanted to know if this discrepancy could explain all the difference in generation and Mr. Megawatt is Frank Todd, manager of Thermal Performance the cause of the problem. Figure 6 shows the plant generation for True North Consulting. True North serves the power industry corrected for the influence of the expected condenser pressure, in the areas of testing, training and plant analysis. Todd’s career, and for the actual condenser pressure. The green line is the difspanning more than 30 years in the power generation industry, has been centered on optimization, efficiency and overall Thermal ference between the two, which is the loss due to the condenser Performance of power generation facilities. You may email him at efficiency problem. email@example.com. Giuseppe was impressed, but we noticed the big guy outside the conference room door was not budging. “So,” Giuseppe said, “yuz told us the ® tomato is bad, but not why the tomato is bad or how we make sauce with the bad tomato. Mr. Gangone, my uncle, would be pleased to know how we fix dis’ problem.” Looking at Brian, I noticed little beads of sweat running down his forehead and knew we had to come up with something TRY quickly. Then I remembered that when I BEFORE was looking at the data I had noticed the YOU BUY! temperature rise across the condenser was a little fishy and I said, “mackerels in the waterbox! 800.536.0790 “Look at this graph (Figure 7),” I continued. “You see the temperature rise across 90° Prism & the condenser is increasing. At a constant • Sharp, Clear Photos & Video Close-Focus thermal input, the condenser temperature • Large 5-inch LCD Monitor tips available! rise should be constant if cooling water flow is not changing. Q = flow x tem• Easy-to-Use Controls perature rise. Since temperature rise is • Annotation Feature increasing and Q is constant, flow must be changing (Figure 8).You told me that your • Rugged Tungsten Sheathing circulating water pumps were just replaced • Quality Construction and are working fine, but something is • Precise 4-Way Articulation changing the flow through the condenser. If it is not the pumps it must be the system • Starting at only $8,995 or the flow area in the tube side condenser. You also told me that the syndicate lost their man on the inside of the EPA and In stock, ready for overnight delivery! they are making you reintroduce mackerels Hawkeye® V2 Video Borescopes are fully portable, to the river.You have waterbox fouling.” finely constructed, and deliver clear, bright high resolution photos and video! The 5” LCD monitor That evening they took a down power, allows comfortable viewing, and intuitive, easy-to-use popped open the water box and started controls provide photo and video capture at the touch CPR on a boat load of mackerels. We sugQuickly inspect cooling tubes of a button! V2’s have a wide, 4-way articulation range, gested that they change the location where inside heat exchangers, turbine and are small, lightweight, and priced starting at only blades, and much more! they were adding the fish to the river and $8995. V2’s are available in both 4 and 6 mm diameters. we set up a monitoring system to identify Optional 90° Prism and Close-Focus adapter tips. future flow problems with the condenser. Made in USA Once again, Brian and I had dodged Visit us at: the cement overshoes and came away with bellies full of pasta and wine. As I pulled into the garage, Mrs. Megawatt was standing there with a decidedly sour look on Booth # 3033 • Orlando, FL May 18 - 21, 2015 gradientlens.com/V2 VIDEO BORESCOPES
Fast, Reliable, Affordable, Visual Inspection!
APRIL 2015 ENERGY-TECH.com
Heat Exchangers – Retrofit/Rebuild/Equipment Upgrade – Bearings – Turbine Tech: Steam – ASME: Combined-Cycle Plants